The FC-RTST LED retrofit kit strip combines high performance LED strips and UL class II LED driver. The FC-RTST accepts 120-277VAC, and delivers 2981 lumens at 30 watts and 4371 lumens at 45 watts respectively. The retrofit is designed to replace 2-lamp and 3-lamp fluorescent troffer fixtures and 2-lamp or 3-lamp strip fixtures.
The kit includes 2/ 3 LED strips and LED driver which can be easily installed with existing fixture.
READ CAREFULLY BEFORE INSTALLING THE RETROFIT KIT. RETAIN THESE INSTRUCTIONS FOR FUTURE REFERENCE
THOROUGHLY INSPECT THE FIXTURE FOR ANY FREIGHT DAMAGE; FREIGHT DAMAGE SHOULD BE REPORTED TO THE DELIVERY CARRIER.
WISDOMLIGHT FC-RTST LED retrofit kits must be wired in accordance with the National Electrical Code and all applicable local codes. Proper grounding is required for safety.
This product MUST be installed in accordance with the applicable installation code by a person familiar with the construction and operation of the product.
User should prepare necessary accessories and spare parts (not provided) including mounting plates, screw driver.
WISDOMLIGHT FC-RTST LED troffer retrofit kit is designed to replace fluorescent lamps within conventional recessed mount fluorescent troffers or surface mount strip fixtures in dry and damp locations.
This installation instruction applies to following models:
Following items are included in this box:
LED retrofit strip, 2 (or 3) pcs
LED driver, 1pcs
“U” brackets, 6 (or 9) pcs
Optional Magnets on U bracket, 6 (or 9) pcs
Lamp replacement marking label, 1pcs Picture is for illustration purpose only.
Installation instruction, 1 set Your model may vary.
RISK OF FIRE OR ELECTRIC SHOCK. Make sure power supply is OFF before installing or maintaining the product.
RISK OF FIRE OR ELECTRIC SHOCK. Install this product only in the luminaires that have the construction features and dimensions shown in the photographs and/or drawings and where the input rating of the product does NOT exceed the input rating of the luminaire.
RISK OF FIRE OR ELECTRIC SHOCK. To prevent wiring damage or abrasion, do not expose wiring to edges of sheet metal or other sharp objects.
RISK OF FIRE OR ELECTRIC SHOCK. LED retrofit kit installation requires knoFCedge of luminaires electrical systems. If not qualified, do not attempt installation. Contact a qualified electrician.
RISK OF FIRE OR ELECTRIC SHOCK. Only those open holes indicated in the photographs and/or drawings may be made or altered as a result of kit installation. Do not make or alter any open holes in an enclosure of wiring or electrical components during installation.
RISK OF FIRE OR ELECTRIC SHOCK. Never perform maintenance or cleaning while fixture is energized. Disconnect power and allow fixture to cool before maintaining.
RISK OF INJURY. Wear safety glasses and gloves during installation and servicing.
The retrofit models are suitable to be installed to the luminaires as shown below.
| Retrofit Model
|| Luminaire Type
|| Minimum Lamp Compartment Size
|| Luminaire Outlook
WIRING DIAGRAM FOR FC-RTST345 (THREE STRIPS)
INSTALLATION INSTRUCTION FOR RECESSED MOUNT TROFFERS
1.Open fixture, remove fluorescent tubes and all other internal components. Disconnect fluorescent ballast from power wires.
2.Align LED strips inside the fixture and locate the points where “U” bracket will be installed. Drill one hole (diameter 4 mm) for each “U” bracket. Install “U” brackets using tek screws into fixture. Once secure, click LED strips into “U” brackets.
3.Align LED driver inside the fixture and locate the area where LED driver will be installed. Drill two holes (diameter 4 mm) and install LED driver using tek screws into fixture.
4.Connect LED strips to LED driver’s output end according to wiring selection.Connect RED lead to driver’s POSITIVE (RED) supply lead; connect BLACK lead to driver’s NEGATIVE (BLACK) supply lead.
5.Connect LED driver’s input end to AC source according to wiring selection. Connect BLACK lead to LINE (+) supply lead; connect WHITE lead to NEUTRAL supply lead.
6.Close fixture and place provided replacement marking label on retrofitted fixture, where visible during re-lamping.
7.Turn on power and enjoy your LED lighting.
Next: 25W Architectural LED Wall Pack